SCOPE OF WORK
Department of Transportation employees were experiencing lack of air flow and an uncomfortable environment. Monster Vac Inspected the HVAC systems and found severe restrictions to air flow located in the Hot water coils. Monster Vac performed restoration work on the coils. Also Monster Vac cleaned and adjusted blowers and the entire air handler. Supply and return air ducts were inspected and cleaned. Turning vanes were cleaned and straightened out. Fusible link was replaced and fire damper repaired where one had fallen out of place. Monster Vac also converted current filtration system to a high efficiency system while at the same time increasing existing air flow. Monster Vac returns every 6 months to address filtration needs and to monitor system performance.
4201 E Arkansas Ave Denver, CO 80222